# Steam Pipes - Sizing

## Pipe sizing steam systems - major and minor loss in steam distribution systems

The pressure available for distribution of steam is the pressure difference between the initial pressure at the boiler, and the required final pressure at the end of the line - at the steam consumer.

The pressure difference available for the distribution system can be expressed as:

p = pj - pk                                    (1)

where

p = available pressure drop (Pa (N/m2), psi (lb/ft2))

pj = initial or boiler pressure (Pa (N/m2), psi (lb/ft2))

pk = final pressure (Pa (N/m2), psi (lb/ft2))

The total pressure drop in the distribution system is a result of friction (major loss) and pressure loss in fittings (minor loss), and can be expressed as:

pt = pmajor + pminor                               (2)

where

pt = total pressure drop in the system (Pa (N/m2), psi (lb/ft2))

pmajor = pressure loss in pipes due to friction (Pa (N/m2), psi (lb/ft2))

pminor = pressure loss in fittings (Pa (N/m2), psi (lb/ft2))

### Friction - Major Loss

Major loss - the pressure loss due to friction in a low pressure steam distribution system can be expressed as:

pmajor = pa l                                (3)

where

pa = pipe friction resistance per unit length of pipe (Pa/m (N/m2/m), psi/ft (lb/ft2/ft))

l = length of pipe (ft, m)

The pressure drop in a steam pipe can be expressed as

pa-100 = 0.01306 q2 (1 + 3.6/di) / (3600 ρ di5)                                      (3b)

where

pa-100 = pressure drop per 100 ft pipe (psig / 100 ft)

q = steam flow rate (lb/h)

di = inside diameter of pipe (in)

ρ = density of steam (lb/ft3)

### Loss due to Fittings - Minor loss

Loss due to fittings - minor loss can be expressed as:

pminor = ξ 1/2ρ v2                                 (4)

where

ξ = minor loss coefficient

pminor = pressure loss (Pa (N/m2), psi (lb/ft2))

ρ = density (kg/m3, slugs/ft3)

v = flow velocity (m/s, ft/s)

### Equivalent length

Minor loss - loss due to fittings can also be expressed as equivalent length:

pminor = pa le                                (5)

or

pt = pa(l + le)                                 (6)

where

le = equivalent length of the fittings (ft, m)

As a rule of thumb the total pressure drop is about 5 -10% of initial pressure per 100 m pipe.

### Typical Steam Velocities

• Exhaust steam - 20 to 30 m/s (70 - 100 ft/s)
• Saturated steam - 30 to 40 m/s (100 - 130 ft/s)
• Superheated steam - 40 to 60 m/s (130 -200 ft/s)

## Related Topics

• Steam and Condensate - Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more
• Pipe Sizing - Sizing steam and condensate pipes - pressure loss, recommended velocity, capacity and more

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!