# Friction Loss in Air Ducts

## Friction loss or major loss in air ducts - equations and online calculator for rectangular and circular ducts - imperial and SI units

Sponsored Links

The major loss, or friction loss, in a circular duct in galvanized steel with turbulent flow can for imperial units be expressed

Δp_{ }= (0.109136 q^{1.9}) / d_{e}^{5.02 }(1)

where

Δp= friction (head or pressure loss) (inches water gauge/100 ft of duct)

d_{e}= equivalent duct diameter (inches)

q= air volume flow - (cfm - cubic feet per minute)

For rectangular ducts the equivalent diameter must be calculated.

### Air Ducts Friction Loss Calculator - Imperial Units

The friction loss calculator below is based on formula *(1)*:

Pressure loss and air flow velocity for some common duct sizes and air flow volumes can be taken from the table below:

Pressure Loss (inches water gauge per 100 feet duct) | |||||||
---|---|---|---|---|---|---|---|

Air velocity (ft/min) | |||||||

Air Volume (cfm) | Duct Size (inches) | ||||||

4 | 5 | 6 | 8 | 10 | 12 | 16 | |

100 | 0.65 | 0.21 | 0.09 | 0.02 | 0.01 | ||

1146 | 733 | 509 | 286 | 183 | |||

200 | 0.8 | 0.32 | 0.08 | 0.02 | 0.01 | ||

1467 | 1019 | 573 | 367 | 255 | |||

400 | 1.19 | 0.28 | 0.09 | 0.04 | 0.01 | ||

2037 | 1146 | 733 | 509 | 286 | |||

800 | 0.34 | 0.14 | 0.03 | ||||

1467 | 1019 | 573 | |||||

1600 | 0.12 | ||||||

1146 |

Air velocity should not exceed certain limits to avoid unacceptable noise generation.

### Air Ducts Friction Loss Calculator - SI Units

The friction loss calculator is based on formula *(1)* with input and output values modified for SI units.

Sponsored Links

## Related Topics

Sponsored Links