# Noise Attenuation in a Chamber

## Chamber noise attenuation

Noise attenuation in a chamber:

dL = 10 log( 1 / Ao (cosθ / 2 π s2  + (1 - α) / (α A)) )                                         (1)

where

dL = sound attenuation (dB)

Ao = outlet area (m2)

A = chamber inside surface area (m2)

θ = angle between inlet and outlet (degrees)

s = distance between inlet and outlet (m)

α = inside surface sound absorption coefficient

### Example - Attenuation in a Chamber

The attenuation in a chamber lined with mineral wool with a sound absorption coefficient α = 0.65, inside surface area A = 16 m2, outlet area Ao = 0.25 m2, distance between inlet and outlet s = 2 m, angle between inlet and outlet α = 45o, can be calculated as

dL = 10 log( 1 / (0.3 m2) (cos45o / 2 π (2 m)2  + (1 - 0.65)/(0.65 (16 m2))) )

= 17.3 dB

## Related Topics

• Noise and Attenuation - Noise is usually defined as unwanted sound - noise, noise generation, silencers and attenuation in HVAC systems

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!