# Fans - Air Temperature and Volume Flow, Pressure Head and Power Consumption

## The temperature and density of the air influences on the volume flow, pressure head and power consumption in a fan

Density of air varies with temperature and pressure (or altitude and elevation above sea level) and a fan will not deliver according manufacture specification if the operating conditions are outside the NTP - Normal Temperature and Pressure Conditions.

### NTP - Normal Temperature and Pressure Conditions

Manufacturers specifications of fans are in general based on the

A fan is a "constant volume" device where the volume in the fan - and the transported air volume through the fan - always is the same (with the same speed and size of the fan).
Since the density of air varies with temperature and pressure the mass flow through a fan varies with temperature and pressure.

• hotter air and lower air density - less mass will be transported through the fan
• colder air and higher air density - more mass will be transported through the fan
• equal speed and dimensions - the volume flow remains equal

When selecting a fan it is important to know if the specification of the system is based on operating conditions or NTP conditions. The formulas below can be used to calculate the volume flow, pressure head and power consumption at NTP conditions if the operating conditions are known, or vice versa if the NTP conditions are known.

The examples below may clarify the procedures:

### Volume Flow

The ratio between the volume flow at different temperatures can be expressed as

qo / qr = (273 + to) / (273 + tr)                                   (1)

or

qo = qr (273 + to) / (273 + tr)                                   (1b)

where

qr = reference volume flow (m3/s)

qo = operating volume flow (m3/s)

tr = reference temperature (oC)

to = operating temperature (oC)

The ratio between developed pressure at different temperatures can be expressed as:

dpo / dpr = (273 + to) / (273 + tr)                                  (2)

or

dpo = dpr (273 + to) / (273 + tr)                                   (2b)

where

dpr = reference pressure developed (Pa)

dpo = operating pressure developed (Pa)

### Power

The ratio between power consumption at different temperatures can be expressed as:

Po / Pr = (273 + tr) / (273 + to)                                       (3)

where

Pr = reference power consumption (W)

Po = operating power consumption (W)

### Volume, Pressure and Power Ratio Chart

The volume, pressure and power ratios are expressed in the chart below. The chart is based on a NTP reference with temperature of 20 oC.

### Volume, Pressure and Power Ratios Calculator

The calculator below can be used to estimate the volume, pressure and power ratios at different temperatures. The default values are based on NTP conditions.

tr - reference temperature (oC)

to - operating temperature (oC)

### Example - Fan with Hot Air

A fan delivers 10000 m3/h of hot air at 60 oC. The total pressure loss in the system at this volume is estimated to 500 Pa.

Decide the correct air volume and pressure for choosing a fan from the manufacturers data. Decide the power consumption.

Since the air volume is estimated for the hot air, the correct volume for the fan is 10000 m3/h.

The pressure coefficient is approximately 1.15 for air at 60 oC according the chart. The correct pressure in the manufacturing data sheet should be

500 x 1.15

= 575 Pa

The power consumption according the manufacturing data is 2.5 kW. The power coefficient is approximately 0.88 for air at 60 oC according the chart. The correct power consumption should be

2.5 kW x 0.88

= 2.2 kW

Note!  - do not compensate the pressure developed by the fan if the pressure loss in the system is estimated on the basis of normal charts based on air with density 1.2 kg/m3.

### Example - Fan with Combustion Air

10000 m3/h of normal standard air at 20 oC shall be transported at an operating combustion air temperature of 180 oC. The total pressure developed at 180 oC is estimated to 500 Pa.

Decide the correct air volume and pressure for choosing the fan from the manufacturers data and decide the total pressure for selecting the fan!

The volume coefficient in the chart above is 1.55 at 180 oC. The operating volume flow for selecting the fan would be

10000 x 1.55

= 15500 m3/h

The pressure coefficient for air at 180 oC is approximately 1.55 according the chart. The correct pressure used in the manufacturing data sheet should be

500 x 1.55

= 775 Pa

The power consumption according the manufacturing data is 4 kW. According the chart the power coefficient is approximately 0.65. The correct power consumption should be

4 kW x 0.65

= 2.6 kW

Note! - the power consumption is lower in operating condition than during start up. A motor (and the motor protection) should in general be big enough to handle higher start up power consumption.

Remember! If a fan starts with temperatures below 20 oC (NTP) - the power consumption will be higher than specified in the catalogue - and the fan may be stopped by the electrical overload protection. The power consumption during start up can be reduced by limiting the volume flow with a closing damper on the outlet of the fan.

## Related Topics

• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more

## Tag Search

• en: fan capacity temperature density
• de: Ventilatorleistung Temperatur Dichte

## Search the Engineering ToolBox

- "Search is the most efficient way to navigate the Engineering ToolBox!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!